Pumped Hydroelectric Storage
Pumped hydroelectric storage facilities storein the form of water in an upper reservoir, pumped from another reservoir at a lower elevation (Figure 1). During periods of high electricity , is generated by releasing the stored water through turbines in the same manner as a conventional hydropower station. During periods of low demand (usually nights or weekends when electricity is also lower cost), the upper reservoir is recharged by using lower-cost electricity from the grid to pump the water back to the upper reservoir.
Reversible pump-turbine/motor-generator assemblies can act as both pumps and turbines. Pumped storage stations are unlike traditional hydroelectric stations in that they are a net consumer of electricity, due to hydraulic andlosses incurred in the of pumping from lower to upper reservoirs. However, these plants are typically highly efficient (round-trip efficiencies reaching greater than 80%) and can prove very beneficial in terms of balancing within the overall power system. Pumped-storage facilities can be very economical due to peak tand price differentials and their potential to provide critical ancillary grid services.
Pumped storage hydroelectric projects have been providing energy storage capacity and transmission grid ancillary benefits in the United States (U.S.) and Europe since the 1920s. Today, the 40 pumped- storage projects operating in the U.S. (shown in Figure 2) provide more than 20 GW, or nearly 2 percent, of theof the electrical supply system (Energy Information Admin, 2007). Table 1 below presents a table of PSH capacities world-wide by country. In 2009, the world’s pumped hydroelectric storage generating capacity was over 100 GW.
Pumped storage hydropower can provide energy-balancing,, storage capacity, and ancillary grid services such as network frequency control and reserves. This is due to the ability of pumped storage plants, like other hydroelectric plants, to respond to potentially large electrical load changes within seconds. Pumped storage historically has been used to balance load on a system, enabling large nuclear or thermal generating sources to operate at peak efficiencies. A pumped storage project would typically be designed to have 6 to 20 hours of hydraulic reservoir storage for operation at. By increasing plant capacity in terms of size and number of units, hydroelectric pumped storage can be concentrated and shaped to match periods of highest demand, when it has the greatest value.
Pumped storage projects also provide ancillary benefits such as firming capacity and reserves (both incremental and decremental),, capability, and spinning reserve. In the generating mode, the turbine-generators can respond very quickly to frequency deviations just as conventional hydro generators can, thus adding to the overall balancing and stability of the grid. In both turbine and pump modes, generator-motor excitation can be varied to contribute to reactive power load and stabilize voltage. When neither generating nor pumping, the machines can be also be operated in mode, or can be operated to provide spinning reserve, providing the ability to quickly pick up load or balance excess generation. Grid-scale pumped storage can provide this type of load-balancing benefit for time spans ranging from seconds to hours with the digitally controlled turbine governors and large water reservoirs for bulk energy storage.